11.1 HEAT STORE TECHNICAL DATA
* This test is performed in the factory on every container before enamelling.
11.2 ELECTRIC ELEMENT DETAILS:
11.4 ELECTRIC BOOSTER RECOVERY TIMES
The table below gives the hours required to electrically heat the listed water quantities from cold to 60C, assuming no solar input. (Container losses included.)
11.5 WEIGHTS AND PIPE CONNECTION SIZES
2500J 3500J 6500J Collector Flow And Return mm 20 25 32 Connection Potable Water Connection mm 32 32 32 Drain And Fill Connection mm 20 20 20 Auxiliary Heating Connection mm 25 25 32 Weight Empty kg 1050 1650 2300 Weight Full kg 3550 5450 9100
11.6 STAND ALONE GAS HEATING ONLY
All models can be installed without collectors and used as gas hot water systems only. This provides a flexibility to add collectors at a later stage. Gas heating may be supplied either for the top half of the Heat Store only (as in solar models) or as a heat source to the entire volume of the Heat Store.
11.7 CLOSED CIRCUIT CORROSION INHIBITOR